ZGXL-MZ1J-24 Signal SPD
Mã sản phẩm :
The ZGXL-MZ1J-24 Signal SPD can be used in the protection of the industrial control network, RS422/485 interface, automatic control and instrumentation lines, data lines, telephones, facsimile apparatus, and other equipment, as well as the sensors and secondary meters in the circuit loop. It can suppress the induced lightning waves from the signal lines, preventing system equipment from indirect lightning strokes.
Features Characterized by the fast response speed (ns) and low protection level, the SPD is hot pluggable, and can be installed on the DIN rail with the connection mode of terminal blocks. Technical Data
- Standards Complied GB/T 18802.21-2004 Low-voltage surge protective devices – Part 21: Surge protective devices connected to telecommunications and signaling networks – Performance requirements and testing methods
Q/75875187-9•3—2011 Signal SPDInstallation, Usage And Maintenance
1 Before connecting the SPD into the system, first check the grounding resistance of grounding grid, which should meet relevant requirements of specifications.
2 Install the SPD on the grounding rail reliably.
3 Unscrew the screws of connecting terminals with a screwdriver, and connect the signal line of system to the input end of SPD, and the output end to protected equipment; ensure a reliable connection of connecting terminals.
Usage and Maintenance
1 There are the IN and OUT markings on the nameplate of SPD, and do not reverse them; otherwise the SPD will be damaged, and equipment cannot be effectively protected.
2 Users cannot disassemble the fastening pieces of SPD at random, in order to avoid damage.